|Joined:||Sat, Apr 4th 1998, 00:00||Roles:||N/A||Moderates:||General discussion about technology and policy|
|Mobile from a Subaru XV||Jun 8th 2015, 18:05||1||686||on 8/6/15|
|T8 Lamps||Sep 20th 2011, 14:56||6||6,796||on 17/6/14|
|Part 15 and Plasma Televisions||Sep 14th 2011, 15:13||2||2,187||on 14/9/11|
|Common-Mode Interference from Cable System||Sep 13th 2011, 15:13||3||2,814||on 25/8/13|
|RFI from HVAC Systems||Sep 1st 2011, 19:08||3||2,562||on 28/1/16|
|RFI from Plasma TV||Sep 1st 2011, 17:20||3||6,807||on 13/9/11|
|Alignment of Vintage Shortwave Receiver - Pilot T-511||Aug 3rd 2011, 13:43||7||4,273||on 5/2/13|
|HF RF Tripping Arc Fault Circuit Interrupters (AFCI's)||W4TL||2 weeks, 6 days ago|
|This is the first report that I've heard of this. When did you first call Eaton? Did you leave a message or try to call again? What is the current status of you complaint? Thanks.|
|RFI and Residential Marijuana Grow Operations||AC0XU||on 4/8/16|
|I will try to help. Please contact me directly by email at firstname.lastname@example.org.
Mike Gruber, W1MG
|HF RF Tripping Arc Fault Circuit Interrupters (AFCI's)||W4TL||on 4/8/16|
|Here is an update on this situation as of today for 2016. We have received a total of five AFCI complaints here at the ARRL since January.
Here is a brief run down on each:
1) Ham was referred to Eaton in February. No further issues were reported.
2) Ham was referred to Eaton in February. No further issues were reported.
3) Complaint involved a non-Eaton breaker. I believe the ham added chokes to mitigate the problem.
4) Ham was referred to Eaton in April. No further issues were reported.
5) Ham was referred to Eaton in June. No further issues were reported.
In summary, each of the four Eaton breaker complaints that we received this year were referred to Eaton for free replacements. After that referral, none of them has reported any further issues. Please also be assured that we are still monitoring the situation.
|ATT U-verse TV system||KF0IQ||on 22/4/16|
|U-Verse customers probably number in the millions by now. Statistically speaking, we've had a surprisingly small number of complaints given from them. Offhand I don't recall any in the last few months and most of the older complaints were resolved.|
|HF RF Tripping Arc Fault Circuit Interrupters (AFCI's)||W4TL||on 17/3/16|
|Assuming that you are operating at HF, ferrite beads are unlikely to fix the problem. I might suggest using ferrite toroids on the speaker leads, especially if this problem can occur even when the stereo is not on. Install the cores as close to the amplifier as practical. A good mix might be type 31 ferrite, but if you can't get it, try type 43. I'd start by wrapping about ten turns or so around the toroid to see what happens. You may also need to add similar chokes and an ac line filter to the power cord of the stereo. I would not think that this problem is directly related to the tripping AFCIs.|